Current transducers (CTs) are a critical component of power monitoring. They come in a variety of formats, sizes, current ratings and accuracy levels. The aspect we would like to focus on here is size, specifically inside diameter.
The inside diameter (ID) is the width of the opening in the CT that the conductor goes through. It must be large enough to fit around the conductor, however choosing too large of a CT can create other issues. As the graphic above indicates, the overall dimensions of the CT grow substantially as the ID gets bigger.
Be sure to use a CT with a current rating as close to the actual current being monitored as possible to maximize accuracy at the lowest possible load. A CT will be accurate across some portion of its range. For example, a 200 amp CT that is +/- 1% accurate might maintain that accuracy from 5% to 120% of its rated capacity (i.e. on loads between 10 and 240 amps).
CTs of the same amperage come in different sizes. For example, Packet Power offers 200 amp CTs with 24mm, 36mm and 50mm IDs. The chart below shows that a 200A CT with a 50mm ID is much larger than one with a 24mm ID. Since space inside electrical equipment is often tight, using a CT that is larger than needed can create problems as well.